Pipeline design errors and poor live pictures
1. Give young pipe design engineers more emotional insights.
2. Let everyone sum up lessons learned and avoid the same mistakes in the future design work.
There is a problem: the flange cover collides with the Pipeline
Problems: Inconvenient maintenance
There is a problem: the height of the emptying tube is not enough and has been modified
There is a problem: the hole is too big （Has already done insulation）
Problems: improper platform height design
There is a problem: bumps and cans collided
There is a problem: the flame arrester is inconvenient to install and maintain
There is a problem: there is a problem with the ground in the buried pipeline
The material used is not correct. After a certain period of time, leakage occurs.
Inconvenient to drain
Pump foundation error
Open hole in weld
The valve group is located between the pipeline and the equipment. The space is small and it is not easy to repair.
Question: Joint support should be set up to facilitate installation and maintenance.
The spacing is too small for easy maintenance
Aisle blocking pipeline
Does not consider the valve installation space, piping error